building has a total area of 44,015 sq. ft. of which
approximately 3% (1,336 sq. ft.) is common area.
floor - Built-out technical space.
Concrete construction utilizing flat slabs with
concrete columns with flared capitals. The floors
are constructed of six to nine inches thick concrete.
The columns spacing is 21 feet x 18 feet.
concrete columns and beams with brick in-fill approximately
3 feet high and 12 inches thick. Windows are original
wood frame construction, with fixed insulating glass.
Partitions are drywall on metal studs. Some ceilings
have suspended acoustical tile in a metal grid system.
Most ceilings are exposed concrete. Floors are a
combination of exposed concrete and vinyl composition
tile. Floor load capacity is 250 pounds.
Building has three 200 ton cooling towers. A heating
and cooling glycol loop circulates through out
the Building to provide water to either water
source heat pumps, for individual office areas,
or self contained air conditioning systems in
each telecommunication area. The
system is provided with back up to assure extended
operation should electric or water services, to
the Building, be interrupted.
A 13KV service with two 2500 KVA XFMR and one 500KVA
XFMR transformer. One 2500KVA XFMR supplies tenants
on the fourth floor. The second 2500KVA XFMR supplies
tenants on the 2nd and 3rd floors. The 500KVA XFMR
supplies common space lighting as well as tenants
on the first floor. All tenants are protected by
emergency generators. There are two generators on
the roof both are Diesel Powered one is 1250KW and
the second is 2000KW. All tenants have their own
Automatic Transfer Switch. Generators are supplied
from an in ground common 4000 gallon fuel tank and
two day tanks on the roof.
Building is equipped with a telephone entry system
with card access. Both fire and security systems
are monitored off site. The Building is protected
with a Radionics security system.
Building is equipped with a building fire alarm
system. There are pull stations located at exits,
smoke detection and horn strobes throughout. The
Building has a sprinkler system and fire pump. Some
tenants have their own suppression systems which
are monitored by the building fire alarm control
2,500 pound hydraulic elevator
4,000 pound freight elevator.
lobby on first floor entered from 24th Street.
has one loading dock area with one 8 x12 ft. overhead
slab. Sheet rubber material covered with slag.
are two approved fire exits.